- Compatible with GreenTrol IAT integrated thermal dispersion airflow/temperature sensors or approved BACnet MS/TP airflow measuring devices
- 24 VAC/DC or MS/TP BACnet binary input activates occupied mode operation
- Provide airflow setpoint control, CO2-DCV or population based-DCV during occupied mode
- Accepts approved BACnet MS/TP CO2 sensors or occupancy counters when DCV is required
- Clamp DCV airflow rates between minimum and maximum airflow limits
- Supports unoccupied airflow setpoint control
- Built-in notification alarms
- Contact closure relay can be assigned to notification alarms or active control mode
- MS/TP BACnet connection
The OAC-4000 can be provided with a single integrated IAT-DI duct probe, one or two integrated IAT-UI or IAT-US universal mount probes or an approved external BACnet MS/TP airflow measurement device.
The OAC-4000 interfaces with approved MS/TP BACnet CO2 sensors and occupancy counters when DCV is required.
The OAC-4000 modulates a proportional damper actuator or variable speed fan (VFD or ECM with analog speed control input) to maintain the outdoor airflow rate when an external binary trigger is active (i.e. occupied mode). The binary trigger is typically is provided by a thermostat or other analog or MS/TP BACnet binary output. The trigger can also be provided by the 24 VAC control signal used when a two-position actuator is provided for outdoor air control (replace the two-position actuator with a proportional actuator).
Advanced logic and airflow measurement improves traditional CO2-DCV when demand control ventilation is required. The OAC-4000 controller resets the outdoor airflow setpoint between user defined minimum and maximum airflow limits to maintain either a user defined fixed CO2 level or variable airflow setpoint based on the population using a built-in CO2/airflow counting algorithm or external occupancy counter.
The OAC-4000 interfaces with most MS/TP BACnet building automation systems and supports full read/write privileges as a BACnet 1/8 load master. An RS-485 signal isolator is available when an isolated MS/TP network is required.
Minimum Outdoor Air Control (MOAC) Modes Supported
FLOW: Maintains a user defined airflow setpoint
CO2: Maintains a user defined CO2 level by resetting the outdoor airflow setpoint (requires a CO2 sensor)
CO2/OAF: Maintains a calculated outdoor airflow setpoint based on the estimated ventilation zone population (requires a CO2 sensor)
COUNT: Maintains a calculated outdoor airflow setpoint based on the occupancy counter population (requires an occupancy counter)
FIXED: Maintains a fixed damper position (no control)
PASS: Passes the economizer controller output signal (no control)
Unoccupied Air Control (UAC) Mode Option: Yes, maintains a user defined airflow setpoint
Economizer Controller Fault Signal Output: Not supported
“Unoccupied Mode” High/Low Airflow Alarm
“Minimum Outdoor Airflow Mode” High/Low Airflow Alarm
“All Modes” CO2 Alarm (requires a CO2 sensor)
“All Modes” System Trouble Alarm
Note: Alarms can be assigned to the contact closure relay
Display: 16-character alpha-numeric LCD
Navigation: 4-button interface
INTEGRATED SENSOR CAPABILITY
Type: Accepts GreenTrol IAT-DI, IAT-UI and IAT-US Thermal Dispersion Airflow and Temperature Measurement Probe (required unless an external MS/TP airflow measurement device is provided). See appropriate IFT product data sheet for probe information.
Available Configurations: IAT-DI Probes
Single Probe: 1 probe x 1 or 2 sensor nodes/probe
Available Configurations: IAT-UI and IAT-US Probes
Single Probe:Dual Probe: 2 probes x 1 sensor node/probe
Dual Probe: 2 probes x 1 sensor node/probe
GENERAL PURPOSE INPUT
Type: Binary Input (BI1)
Assignment: Mode activation trigger signal
Configurable Ranges: 0-24VAC or 0-24VDC
VAC Configuration: 7 VAC
VAC Configuration: 3 VAC
Assignment: Airflow control signal
Configurable Ranges: 0-5V, 0-10V, 2-10V, or 4-20mA
Maximum Number of Actuators Supported:
0-5V, 0-10V or 2-10 V: Unlimited
CONTACT CLOSURE RELAY
Type: Dry contact w/ onboard jumper to drive a remote LED
Assignment: OAC alarms or Control Mode
Status: Normally Open (N.O.)
Rating: 30 VDC or 24 VAC @ 3 amp. max.
Type: Non-isolated MS/TP BACnet master connection (provide an RS-485 network isolator if isolation is required)
B.A.S. Object Read/Write Access: Yes
Device Load: 1/8 load
Supported Baud Rates: 9.6, 19.2, 38.4 and 76.8 kbaud
MS/TP BACnet Airflow Sensor Capability: One GreenTrol Automation or approved third-party airflow measurement device (cannot be used if an integrated airflow measurement device is connected).
MS/TP BACnet CO2 Sensor Capability: One GreenTrol Automation or approved third-party space mounted or return air CO2 sensor
MS/TP BACnet Occupancy Counter Capability: One to four GreenTrol Automation or approved third-party occupancy counterssensor
ENVIRONMENTAL LIMITS, POWER REQUIREMENTS & DIMENSIONS
Temperature: -20 to 120 ⁰F [-28.9 to 48.9 ⁰C]
Humidity: 5 to 95%
Important: Provide a weather-proof enclosure if the controller module is mounted outdoors
Power Requirement: 24 VAC (22.8 to 26.4 under load) @8.5V-A
Dimensions: 4.34H x 6.59W x 1.83D in. [110.2 x 167.3 x 46.6 mm]